Electricians often need conduit benders and other bending tools to form electrical conduit and pipe to make it fit where it is needed. When used properly, they make accurate and consistent bends without damaging the conduit.
There are a wide variety of benders available. From hand operated tools to larger benders for forming electrical metallic tubing, intermediate electrical conduit, rigid piping and PVC conduit. The type you need largely depends on the size and type of conduit you are working with and how much bending needs to be done.
EMT, IMC and rigid piping needs a bender with a bending shoe. There is a groove in the bending shoe that matches the outside diameter of the conduit and supports the inner radius and outer wall as the bend is formed. For PVC conduit, you need a bender with a heating component to soften the plastic so it can be shaped the way you want.
Hand operated benders are the simplest in design and have changed very little over the years.
It is basically a shoe and a handle that rolls the conduit between the floor and the tool, gradually increasing the bend as it rolls. Shoes for hand benders are available in sizes from ½ inch to 1 ½ inches in diameter.
Hand operated conduit benders include Gardner-style and Benfield-style models. Both models work the same, but Benfield models are made of iron and are marked with bend angle reference points.
Gardner models are made of die cast aluminum and have built in spirit levels to indicate 45 and 90 degree angles. For extremely tight radii, you would use a Hickey bender.
This type of bender is a step up from hand benders. It still takes manual force to make the bend, however they do have several features that make them more convenient. The unit is mounted to a small carriage that you can easily roll to wherever you need it and it has a platform at a comfortable height.
Some models have a removable frame so you can mount it to your workbench or truck bed. There are several interchangeable shoes to accommodate various types and sizes of conduit. Most mechanical benders can handle ½ inch to 2 inch IMC, EMT, rigid piping and PVC coated conduit.
For high production conduit bending, you need an electric model. These types can handle the same types and sizes of conduit as the hand operated and mechanical models, but work much faster. They can make a bend in seconds.
Some electric models can bend several sizes of IMC, rigid piping and rigid aluminum without changing or adding shoes. Other types of pipe require different shoes.
You can program an electric bender to make the same bends over and over and it is able to calculate layout measurements for different bends before work starts.
When you have rigid electrical conduit from 2 ½ to 5 inches, you need a hydraulic bender. Electric benders can't make a smooth bend on pipes this large without squeezing, splitting or bulging the conduit. This type of bender is powered by a manual or electric hydraulic pump. Compact models for pipes 1 to 2 inches in diameter are also available. Hydraulic conduit benders can be adapted for conduit coated with PVC.
PVC must be softened before it can be bent. Once softened, you use a guide device and hand gauge to form elbows, bends and offsets. Heating tools most commonly used to heat the PVC include tubes, boxes and blankets. You can place the conduit inside a heating box until it is soft enough. Blanket heaters are often used on conduit that is already installed and for custom bends.
Aside from the conduit bender, there are few other tools you will need for professional results.
You will need:
First, you need to determine how long the bend needs to be. For example, say you are running a ¾ inch pipe down the wall and need to run it into a box 12 inches away from the wall. From the start arrow to the back of the bending shoe there is a 6 inch take up, so you need to measure six inches from the end of the pipe and mark the point with your pencil. This six inches plus the six inch take up will give you the 12 inches you need.
On the front, right side of the bender shoe, you will see an arrow. Line this arrow up with the line you made on the pipe. Before you begin bending, check to see if the floor is level. A level floor makes the process easier.
Take hold of the handle and pull it back towards you. While you are pulling, apply pressure on the heel of the bender shoe with your foot. On the side of the shoe you will see 30, 60 and 90 degree markings. Once your bender reaches the 90 degree mark, your bend is complete.
When using conduit benders, always make sure to keep firm pressure on the back of the shoe. If you don't, it can slip on the pipe and your measurement will be way off.